Week of Aug. 11
Andrew Mancini Associates set all the door frames, completed most of the block partition walls, and started ceramic tile installation in the bathrooms. Workers started sanding the gym floor and assembling the bleachers in the cafeteria. Ceiling tile installation in the hallways and cafeteria has begun. A roofer was on site making penetrations for the exhaust fans and air handlers for the bathrooms and library.
Window lintel replacement continued in the window openings in the hallways, as did flooring installation in the second floor classrooms.
Digesare started assembly of the air handler for the cafeteria and installing duct work for the exhaust fans. Workers continued temperature control work as well as valve and steam trap replacement.
Nelcorp finished installation of the new fire alarm system and removing the old one. Workers installed new panel boxes for the stage lighting and continue conduit and wiring in the cafeteria.
Tri-Valley completed rough-in for plumbing fixtures in all the bathrooms.
Posted: Friday, August 11, 2017